Particles from One Transformer
All of the particles that follow are from one 50 milliliter oil sample collected from a 8400 kVA
Transformer. The transformer reportedly had a gas blanket and was sealed. The particles indicate
otherwise. The large number of degraded paper fibers in this sample indicate severe degradation of
the paper insulation and there is evidence of charring of the paper at some locations.